The Auto-Response facility (in all console servers with Firmware V3.5.1 and later) monitors nominated ports/ devices / probes/ states for Check Condition to trigger action sequences. To use the properties of any attached UPS as the trigger event:
- Select UPS Power Device Property (Input Voltage, Battery Charge %, Load %, Input Frequency Hz or Temperature in °C) that will checked for the trigger
- Specify the Trigger value that the check measurement must exceed or drop below to trigger the AutoResponse
- Select Comparison type as being Above Trigger Value or Below Trigger Value to trigger
- Specify any Hysteresis factor that is to be applied to environmental measurements (e.g. if an Auto-Response was set up with a trigger event of a battery charge below 20% with a Hysteresis of 5 then the trigger condition would not be seen as having been resolved till the battery charge was above 25%)
- Check Save Auto-Response
Note: Before configuring UPS checks in Auto-Response you first must configure the attached UPS .
Note: For general info on monitoring, auto-response (and alert config pre V3.5.1) refer faq409-Auto-Response-Alerts